Air-Cooled Jumper Cables FOR SALE
IN-STOCK Limited Inventory Pricing Available
Air-cooled jumper cables are IN-STOCK and FOR SALE at Weld Systems Integrators. Air-cooled jumpers are used to connect high-current, low-voltage applications such as connecting transformer secondaries to weld guns, replacements for flexible laminations, fuel cells, furnaces, induction heaters, many high current, low voltage applications where a flexible connection is required.
Air-cooled jumper cables are available in circular mil sizes from 400 – 2000 MCM (standard). Our in-house engineering team can assist with custom designs, unique customer sizes, and extra-flexible cables.
Click the blue “IN-STOCK Inventory” box below for all available air-cooled jumper cables.
Air-Cooled Jumper Cables IN-STOCK: 33
Contact Weld Systems Integrators at 844-WSI-WELD or +1-216-475-5629 for Special Pricing on all IN-STOCK Air-Cooled Jumper Cables.
Enter Stock / Serial #: “Air-Cooled Jumper Cables” on the following quote request form.
Step 1: Lay one side of a straight edge across the graph at the six cycles of the current “one-time” point (the left-hand vertical scale of the conversion factor chart).
Step 2: Pivot the other end of the straight edge across to line up with the “60 welds per minute” on the far right vertical scale.
Step 3: At the intersection of your straight edge with the diagonal conversion factor scale line, you should be able to read a conversion factor of .32 off the lower 1/2 of the line.
Step 4: Multiply the required current (10,000 amps) by the conversion factor (.32) to get the “continuous duty current” of 3,200 amps. Now proceed to the Air-Cooled Jumper Selection Chart to read and complete the selection.
Step 5: Line up your straight edge on the 3200 continuous duty amp mark, and find the intersection with your desired length line (from below).
Step 6: Any cable whose line is above this point may be safely used since the load it would carry will be within its thermal capacity. In this example, a 1200 MCM cable can be used and stay within design tolerances.
To get LENGTH, measure from the center of one set of mounting holes to the center of the second set.
The secondary measurement, B, is the face width.
The terminal thickness is dependent on the terminal face width, and the gauge of the cable, as outlined in the table on the right.
Standard 1.5″ width will be supplied up to and including 1200 MCM. 1500 MCM comes in 1.375″ width. 2000 MCM in 1.5″ width. Please specify when ordering. Terminal Length: The contact surface length is 1-9/16″. Other lengths can be furnished if specially ordered. Bolt Hole Size: All Air-Cooled Jumpers are drilled with 17/32” bolt holes unless ordered otherwise.
|AIR-COOLED JUMPER CABLES|
|MCM||1-1/4″ Wide||1-3/8″ Wide||1-1/2″ Wide|
|600||1/2″ Thick||7/16″ Thick||–|
|750||5/8″ Thick||9/16″ Thick||–|
|1000||3/4″ Thick||11/16″ Thick||5/8″ Thick|
|1200||7/8″ Thick||13/16″ Thick||3/4″ Thick|
|1500||–||11/16″ Thick||1″ Thick|